These cables particularly for use in fresh water up to 10 m depth with a maximum water temperature up to 40°C , such as the connection of submersible pumps or similar applications. Not suitable for underwater power transmission or installation in a watercourse, or where it is possible that mechanical damage might occur and cause a hazard. Indirect underground installation is allowed provided that there is mechanically protection of the cables. These cables are manufactured according to the Standard and Approval CEI 20-19/16 (CENELEC HD 22.16). It is the only cable that the installation Standard and Approval CEI 64-8 at section 702 allows for installation in swimming pools and fountains. For connections liable to moderate mechanical stresses, i.e.
HD22.16 S1, VDE-0282 Part-16, CEI 20-19 p.16, CE low voltage directive 73/23/EEC & 93/68/EEC., ROHS compliant
|Working voltage:||450/750 volts||Test voltage:||2500 volts||Flexing bending radius:||6.0 x Ø||Fixed bending radius:||4.0 x Ø||Flexing Temperature:||-25º C to +60º C||Fixed Temperature:||-40º C to +60º C||Max Water Temperature:||+40º C||Short circuit temperature:||+250 º C||Flame retardant:||IEC 60332.1|
- Fine bare copper strands
- Strands to VDE-0295 Class-5, IEC 60228 Class-5
- Rubber core insulation EI4 to VDE-0282 Part-1
- Color code VDE-0293-308 and HD 186
- Polychloroprene rubber (neoprene) jacket EM2